Technical Service Bulletin
Issue: DHW and external heat demand not working
Applies to: Vitodens 200, WB2B Series (all models)
The information in this bulletin is intended exclusively for licensed heating contractors, and is NOT intended for the end user. This material is NOT intended to take the place of the information contained in the manuals shipped with the product.
Use of this information by unqualified personnel may result in property damage, personal injury or death.
End users are asked to contact a qualified contractor for all installation and service work. If you need assistance finding a contractor in your area, contact your Viessmann Sales Representative, or use our Contractor Locator.
By hitting "Yes" below you confirm that you have read, understood and agree to this warning, that you are licensed and hold the current, appropriate licences to work on said equipment in the location and/or jurisdiction of installation.
Boiler operates in relay test mode.
DHW pump is not starting on a DHW call.
External heat demand is on but the boiler is not starting.
Fault "CE" is displayed, or coding address "2E" is set to "0".
No communication between the Power Pump Module and the boiler control through the KM-Bus plug 145.
Check the 145 plug connection on the boiler control and in the Power Pump Module.
Re-check coding address "2E". If the value at address "2E" has not changed to "1", then turn power off to the Power Pump Module.
Turn the boiler off, remove the 145 plug from the boiler control, and cut off the plug. Then reconnect the wires to X3 terminals 6 and 7. (This is another connection point for the KM-Bus.) Turn the boiler on and check coding address "2E" again – it should be set to "1". Now the boiler should be communicating with the Power Pump Module.